Chandler, AZ Heating and Air Conditioning Services
Morehart Air Conditioning & Heating provides heater and air conditioning repair, installation and services in Chandler, AZ and surrounding areas.
Check out what some of our customers are saying about Morehart Air Conditioning & Heating services.
for Chandler, AZ
Jusy - Chandler, AZ
Very nice technician and super easy
Kelly - Chandler, AZ
Leo was very friendly and professional, even dusted my vent for me!
In Chandler, AZ: Completed service in accordance with maintenance checklist. Please refer to list for photos and ratings. Cut exposed lineset flush with wall and sealed with silicone. Strapped line together so the liquid lines would stop rubbing on the ground.
In Chandler, AZ: Made scoop for unit 1 float. Lowered water pressure. Made scoop for unit 3 lowered water pressure. No leaks upon departure.
In Chandler, AZ: At a local commercial building to install 3/8 inch brass cooler floats.
In Chandler, AZ: UPON ARRIVAL CYCLED UNITS INTO COOLING MODE. REPLACED INTAKE FILTERS AND TOOK TEMPERATURE READINGS FROM SUPPLY AND RETURN. AT UNITS CLEANED AND TIGHTENED ELECTRICAL CONNECTIONS. TOOK VOLTS AND AMP DRAWS FROM COMPONENTS. CHECKED START AND RUN CAPACITORS. CHECKED FREON LEVELS WITH SUPER HEAT AND SUBCOOL. WASHED AND RINSED OUTDOOR COILS. UPON DEPARTURE UNIT WORKING PROPERLY AND WITHIN MANUFACTURER SPECIFICATIONS.
In Chandler, AZ: UPON ARRIVAL CYCLED COOLERS ON. FOUND WATER LINES SHUT OFF TO THREE SYSTEMS. TURNED WATER ON. FOUND FLOAT IN COOLER 5 OFF. SET FLOATS ON SYSTEMS. ELECTRICAL PANEL FOR COOLER 4 WAS OFF, TURNED ON. CLEAN OUT FITTINGS ON COOLERS WERE LEAKING. SEALED AND TIGHTENED. RECOMMEND REPLACING OEM 3/8 FLOATS IN ALL COOLERS AND DOING REGULAR MAINTENANCE ON SYSTEMS. SERVICE COMPLETED.
In Chandler, AZ: UPON ARRIVAL CYCLED UNIT INTO COOLING MODE. AT UNIT NOTICED COMPRESSOR INOPERABLE. REPLACED DUAL RUN CAPACITOR DUE TO EXISTING ONE OUT OF TOLERANCE . UPON DEPARTURE UNIT WORKING PROPERLY AND WITHIN MANUFACTURER SPECIFICATIONS.
In Chandler, AZ: Upon arrival inspected smoke alarms. Quick red flash is normal operation. It does not mean batteries are low. Explained to customer there is only reason to have concern if it is solid red or chirping. Replaced 9v in all smoke alarms. Customer also wanted clock adjusted on thermostat. Service completed.
In Chandler Az servicing a customers system. Checked volt and amp draws. Cleaned and tightened electrical connections. Checked Freon levels and pressures. Acid washed outdoor coil and changed return filters.
In Sun Lakes Az servicing a customers system everything looks good. Checked volt and amp draws. Checked Freon levels and pressures. Cleaned and tightened electrical connections and changed the return air filter.
In Phoenix Az for a no heat call. Found a bad blower on the unit. Ordered blower from the factory. Going to return to install tomorrow when the motor comes in
In Chandler AZ , performing heating maintenance on two Amana inverter heat pump split systems .