El Mirage, AZ Heating and Air Conditioning Services
Morehart Air Conditioning & Heating provides heater and air conditioning repair, installation and services in El Mirage, AZ and surrounding areas.
Check out what some of our customers are saying about Morehart Air Conditioning & Heating services.
for El Mirage, AZ
In El Mirage: Performed quality inspection on newly installed 5 ton, gas attic split system. Removed existing sheet metal plate in plenum box that services front rooms. Also replaced low voltage wiring at condenser. Noticed oil on insul-tube; performed leak check and observed no leak present; replaced insul-tube. Upon departure, unit is working properly and within manufacturer specifications.
In El Mirage, AZ: Upon arrival, cycled units into cooling mode. Replaced intake filters and took temperature readings from supply and returns. At units, cleaned and tightened electrical connections. Took volts and amp draws from components. Upon departure, 6 units working properly and within manufacturer specifications.
In El Mirage, AZ: PENDING HOMEOWNER APPROVAL ON REPLACING HVAC EQUIPMENT.
In El Mirage, AZ: UPON ARRIVAL CYCLED UNIT INTO COOLING MODE. AT THE CONDENSER TOOK VOLTS AND AMP DRAWS FROM COMPONENTS. CLEANED AND TIGHTENED ELECTRICAL COMPONENTS. CHECKED FREON LEVELS WITH SUPER HEAT AND SUBCOOL. WASHED AND RINSED OUTDOOR COILS. SEALS TO OUTDOOR MOTOR ARE LEAKING OIL AND FAN MOTOR GETTING EXTREMELY HOT (RECOMMEND REPLACING). ALSO COMPRESSOR MAX RATED AMPS 25RLA ACTUAL AMPS ARE 23.62 AMPS. RECOMMEND UPGRADING HVAC EQUIPMENT. HOMEOWNER HAS HOME WARRANTY.
In El Mirage, AZ: Morehart ac to modify ducting into two bedrooms. Modification will cover join 12 in run that current gas a 12x12x10 t with a 12 inch collar. We will the reroute and mount ten inch run directly to supply plenum with ten inch collar. Customer is also interested in having service performed.
In El Mirage, AZ: UPON ARRIVAL CYCLED UNIT INTO COOLING MODE. AT ELECTRICAL CABINET ON THE UNIT FOUND ALL ELECTRICAL BURNED AS WELL AS CONTACTOR. REPLACED CONTACTOR AND WIRING ALSO REPLACED CAPACITOR UNDER PARTS AND LABOR WARRANTY . UPON DEPARTURE UNIT WORKING PROPERLY AND WITHIN MANUFACTURER SPECIFICATIONS.
In El Mirage, AZ: CYCLED SYSTEM ON IN COOLING. CHECKED VOLT AND AMP DRAWS, ALL IN FACTORY SPECIFICATION. CLEANED AND TIGHTENED ELECTRICAL CONNECTIONS. CHECKED FREON LEVELS AND PRESSURES, ALSO IN FACTORY SPECIFICATION. (SEE COOLING CHECKLIST FOR DETAILS). ACID WASHED OUTDOOR COIL AND RINSED. CHANGED RETURN AIR FILTER AND CHECKED SPLITS, RETURN 73 SUPPLY 54. SYSTEM IS OPERATIONAL AT THIS TIME.
In El Mirage, AZ: Upon arrival found distribution line broke in half. Spider line assembly will need to be replaced. In addition pump is seized. There is very heavy build up on pads. Customer is undecided if she wants to replace herself or not. Float is operational. Completed service but unit needs repairs listed in estimate to make it functional. Cooler is in very poor condition for being less than a year old. Recommended having some filtration installed on home as well as adding a clean machine to system. Pending approval.
In the Pueblo El Mirage golf course area. Changing out supply and return boxes because customers was getting a water built up from not having insulated plenum boxes