Gilbert, AZ Heating and Air Conditioning Services
Morehart Air Conditioning & Heating provides heater and air conditioning repair, installation and services in Gilbert, AZ and surrounding areas.
Check out what some of our customers are saying about Morehart Air Conditioning & Heating services.
for Gilbert, AZ
In Gilbert, AZ: ESTIMATE- Provided homeowner with an estimate on installing mini split. Pending approval from homeowner. Service complete.
In Gilbert, AZ: Estimate: Morehart AC to install and furnish 2, three ton gas split systems. To include new secondary pan, wet switches, thermostats, disconnect box, whip kits, flue piping, and gas flex line. To hook up to existing high volt, low volt. ducting, and line set.
In Gilbert, AZ: Upon arrival, cycled units into cooling mode. Took temperature readings from supply and return. Homeowner declined filter replacement or being left with intake filters. At units, cleaned and tightened electrical connections. Took volts and amp draws from components. Checked Freon levels with super heat and subcool. Upon departure, units are working properly and within manufacturer specifications.
In Gilbert, AZ: Upon arrival, cycled unit into cooling mode. At the outdoor unit, noticed compressor inoperable. After diagnosis, found capacitor out of spec. Replaced 80/5 capacitor. Upon departure, unit is working properly and within specs.
In Gilbert, AZ: UPON ARRIVAL CYCLED UNIT INTO COOLING MODE. REPLACED INTAKE FILTERS AND ALSO TOOK TEMPERATURE READINGS FROM SUPPLY AND RETURN. CLEANED AND TIGHTENED ELECTRICAL CONNECTIONS. TOOK VOLTS AND AMP DRAWS. CHECKED FREON LEVELS AND CAPACITORS. UPON DEPARTURE UNIT WORKING PROPERLY AND WITHIN SPEC.
In Gilbert, just re-piped two PVC drain lines on this beautiful commercial building. Unit was leaking water now the unit is repaired and no leaks are occurring.