Scottsdale, AZ Heating and Air Conditioning Services
Morehart Air Conditioning & Heating provides heater and air conditioning repair, installation and services in Scottsdale, AZ and surrounding areas.
Check out what some of our customers are saying about Morehart Air Conditioning & Heating services.
for Scottsdale, AZ
Micaela - Scottsdale, AZ
Eric - Scottsdale, AZ
Questions answered and serviced explained
Always a great service
Allen - Scottsdale, AZ
On time and gets his work done.
Malinda - Scottsdale, AZ
Great service, professionalism, and price
Greg - Scottsdale, AZ
Brian is super as always.
Exceptional customer service
Emily - Scottsdale, AZ
I was fortunate to have my warranty company recommend Morehart four years ago. I have never been more confident in a service industry company than I am in Morehart. I’ve has several technicians out, including the owner himself. Each one has been phenomenal. My most recent experience was with Tom Greene. He’s helped me before, so I’m always happy to see him. He, as usual, went above and beyond today. He was on time, thorough, completely honest with me, and ethical to the highest degree. He could have easily talked me into a part that was not truly necessary, but he treated me like a good friend and gave me the best advice. I can not recommend Morehart more.
Reliable, knowledgeable, great service in both installation & maintenance of equipment!
Mona - Scottsdale, AZ
Response from Morehart Air Conditioning & Heating:
Thank you so much for you feed back! We value and appreciate you as our customer!
Eric - Scottsdale, AZ
On time, friendly, and took care of the problem
In Gainey ranch Scottsdale Arizona performing cooling maintenance on two heat pump carrier split systems
In Scottsdale Az servicing 2 systems 1 is a newer Lennox and the other is an old Arcoire that is in need of some repairs found a 0.0 MFD Capacitors contactor is burnt and pitted. Talked to the cisstimer about replacing the parts.
In Scottsdale, AZ upon arrival changed two April Air 5 Inch filters. Cleaned drains. Down stairs system I replaced the batteries in the thermostat and also found that the units Run Capacitor was out of specs and replaced it at the time of service. Unit is working great upon departure.
In Scottsdale Az servicing a customer new Amana systems we just installed. Checked volt and amp draws. Cleaned and tightened electrical connections. Checked Freon levels and pressures. Changed return air filters and acid washed the outdoor coils. Systems look and run excellent.
In Scottsdale Az servicing two new Amana. Systems we installed last year. Checked volt and amp draws. Cleaned and tightened electrical connections. Checked Freon levels and pressures . Changed return filters and acid washed outdoor coils.
In Scottsdale Az servicing a customers 6 Amana Systems we installed 4 Years ago. Checked volt and amp draws. Cleaned and tightened electrical connections. Checked Freon levels and pressures. Changed return filters and washed outdoor coils. Systems are all running perfect at this time.
Performing heating / cooling maintenance on two amana 16 seer heat pump splits
In Scottsdale, cycled six units into heating mode. Replaced intake filter and took temperature readings from supply and return. Cleaned and tightened electrical connections. Took volts and AMP draws. Vacuumed and wiped down cabinet. Unit is working within manufactures specs.
In Scottsdale servicing a current contract customers 3 systems. Checked burners. Cleaned flame sensor. Checked water column on gas valve and changed the filters.
In Scottsdale servicing 3 units and a water heater. Checked volt and amp draws. Water heater is newer and running good as well.
In Scottsdale performing a tune up on a new Amana we put in last month. Completed first burn off on the furnace. Changed the return air filter. Volt and amps look good. Cleaned and tightened electrical connections. Ready for winter.
In Scottsdale servicing two units for a current contract customer. Checked gas valve adjustment. Vacuumed out burners and furnace cabinet. Removed and cleaned flame sensor and changed return air filters.
In Scottsdale servicing a contract customers systems. Cleaned and tightened electrical connections. Checked volt and amp draws. Checked Freon levels and pressures. Changed return air filter and had to clear out a condensate line because of blockage customer is ready for the seasons ahead.
Changing warn out pvc for a package unit in the Sereno Park area in Scottsdale.
Arrived to customers home and found that the fan motor needed to be replaced. Replaced the fan motor and unit is back up and running upon departure.
In Scottsdale, installing new Amana 5 ton 16 seer gas split system!
In Scottsdale, working on a broken down unit! Replaced the run capacitor and the unit is back to cooling!
In Scottsdale, installing a 7/3 motor, reinstalled line set and also found that the batteries in the thermostat were blown which caused the low volt fuse to blow as well! Once repairs were made to the system, the system is now back up and running!
At a sandwich shop in Scottsdale. Found that the Trane system was very low on freon and that the coil had a leak at the line from the TXV. I was able to weld the line shut, vacuum the system, and recharge unit with 13.8 pounds of R410A.
Build up in coils can damage your HVAC system. This customer in Scottsdale is making sure she is cleaning her coils on her 4 York systems before the major hot months!