Sun City, AZ Heating and Air Conditioning Services
Morehart Air Conditioning & Heating provides heater and air conditioning repair, installation and services in Sun City, AZ and surrounding areas.
Check out what some of our customers are saying about Morehart Air Conditioning & Heating services.
for Sun City, AZ
Fall / Winter Check-up
Cheryl - Sun City, AZ
Brian came to ensure that my systems were ready for the fall/winter season. His professionalism and caring shown through again on this visit. Have been with you all for over 20 years and always treated with respect.
On time, pleasant, and considerate
Kathy - Sun City, AZ
In Sun City Arizona performing heating maintenance on a Trane gas furnace
In Sun City servicing a customers Gas Package unit on the roof. Cleaned out the burners. Adjusted the gas valve and removed and cleaned the flame sensor. Unit is running to factory specification.
New amana service
Installing a new gas package unit near the Riverview Golf course in Sun City.
Installing a new Amana 4 ton in Sun city
In Sun City repairing a Ruud Gas pack unit the liquid right cane apart had to redo the high voltage liquid tight and installed a clamp on it all complete.
In Sun City servicing a gas package system on the roof. Cleaned out the burners, removed and cleaned the flame sensor. Checked volt and amp draws and adjusted the gas valve pressure. All ready for the cold months ahead.
In Sun City, servicing a Newer Amana. Cleaned out the burners. Removed and cleaned the flame sensor. Adjusted the water column on the gas valve. Cleaned and tightened electrical connections, changed the return air filter and checked all safety’s on the furnace.
In Sun City servicing a newer Amana Gas Pack we installed 4 years ago. Checked and cleaned out burner assembly. Checked all safety’s on the system. Cleaned and tightened electrical connections. Checked gas line for leaks and checked volt and amp draws. Unit is running perfect and ready for winter.
In Sun City servicing a unit for a current contract customer. Cleaned out the burners. Checked safety switches. Removed and cleaned the flame sensor. Set gas valve unit is looking good
In Sun City, customer had concerns about noise from the unit. Found accumulator on the unit vibrating against the coil re-tightened the bolt on the accumulators the noise is gone talked to customer about a future replacement because of the age of the system.
In Sun City for a noise equipment call. Found outdoor fan motor locking up. Unit need a new 1/5 Horse 1075 motor and 7.5/440 run capacitor
In Sun City, upon arrival cycled unit tho cooling mode and noticed the temperature splits were below manufactures specifications. Checked the freon levels with the super heat and the subcool. The refrigerant levels were also below manufactures specs. Tested the coil with soap bubbles and found bubbling on the coil. Coil replacement is set to take place this week!
In Sun City doing a tune upon a current customers air conditioner. Unit is In great condition we service it all the time.